This board is for PLC Related Q&A ONLY. Please DON'T use it for advertising, etc.
|Try our online
PLC Simulator- FREE.
Click here now to try it.
New Here? Please read this important info!!!
|October 7th, 2005, 02:26 PM||#1|
Join Date: Oct 2005
Location: York, ME
PLC5 4-20ma input Scaling
I have a 4-20ma input to a 1794-IE8 Flex I/O module. The Flex I/O is talking to a PLC5/40. What is the correct value to use when scaling the raw value. This circuit is measuring water flow in gal/min, and has a max value of 1000 gal/min.
|Currently Active Users Viewing This Thread: 1 (0 members and 1 guests)|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Modicon Analog input scaling..||jimdi4||LIVE PLC Questions And Answers||3||August 23rd, 2004 10:32 AM|
|analog input work on ab plc5||yam785||LIVE PLC Questions And Answers||1||July 9th, 2004 05:34 PM|
|PID output scaling PLC5||russrmartin||LIVE PLC Questions And Answers||2||January 30th, 2004 04:45 PM|
|analog input scaling?||Fred Chwalek||LIVE PLC Questions And Answers||2||December 4th, 2003 05:16 AM|
|A/B Analog Input Scaling||WhatThe||LIVE PLC Questions And Answers||18||November 28th, 2003 06:24 PM|