This board is for PLC Related Q&A ONLY. Please DON'T use it for advertising, etc.
|Try our online
PLC Simulator- FREE.
Click here now to try it.
New Here? Please read this important info!!!
|February 24th, 2004, 10:26 PM||#1|
Transfer restrictions when using Siemens Moby I
I wonder if someone here is familiar with the Simens Moby I (RFID)system?
I'm trying to write 50 bytes to an MDS403 (8Kb) memory tag over an ASM450 unit controlled from a 316DP2 CPU, but so far it only allowes me to transfer 30 bytes. As soon as I pass that limit it'll report the following error:
-> Input or output areas are too small for the telegram length used.
-> Read or write command with excessive length used
-> Adjust bus configuration of the master module.
I have used the same system with the same code to read / write 50 bytes of data before, the only difference was that I used a 413 CPU in that application.
Anyone have som toughts about this?
Failure is not an option
|Currently Active Users Viewing This Thread: 1 (0 members and 1 guests)|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Siemens Profibus To Micromaster 440||jimdi4||LIVE PLC Questions And Answers||17||June 25th, 2011 01:09 AM|
|Acces Siemens S7-315 by VB||GAEvakYD||LIVE PLC Questions And Answers||13||October 14th, 2008 09:29 AM|
|Siemens S5 cpu problem||MagCarb||LIVE PLC Questions And Answers||13||June 15th, 2007 07:34 AM|
|Problems with Siemens MMC cards||RMA||LIVE PLC Questions And Answers||8||November 24th, 2006 02:52 AM|
|Siemens S7-313 to OP270B Communication||qee||LIVE PLC Questions And Answers||4||December 18th, 2003 06:40 AM|