This board is for PLC Related Q&A ONLY. Please DON'T use it for advertising, etc.
|Try our online
PLC Simulator- FREE.
Click here now to try it.
New Here? Please read this important info!!!
|April 20th, 2017, 06:48 PM||#1|
Join Date: Apr 2017
Making a connection between Productivity 3000 and AB 1734-AENTR Remove I/O
I currently have a project that needs to use AutomationDirect Productivity 3000 PAC to communicate with Allen Bradley 1734-AENTR remote I/O module.
I don't have any AB PLCs, or RSLogix 5000 programming software, but I do have Wonderware Intouch available.
Productivity 3000 PAC has the so-called "scanner" feature, so that I can simply create a generic scanner client to retrieve 1734 data.
However, by following this doc: http://literature.rockwellautomation...m016_-en-p.pdf
I didn't get the luck to make them connected.
On my scanner configuration, I put 100 as the Assembly Instance under T->0(Input), and 101 under O->T(output). Is this correct? I am confusing actually.
The PDF says I don't need a configuration header to make a connection. No matter I create this config file or not, I always get the following error:
Connection Resonse: True
Connecting Device: 1734-AENTR/B Et (seems they did exchange info once)
RemoteI/O Online: False
RemoteI/O Status: 1
RemoteI/O Status Description: Invalid segment
Is there anyone got expedience to set up this 1734 remote io?
Thanks a lot!
|Currently Active Users Viewing This Thread: 1 (0 members and 1 guests)|