This board is for PLC Related Q&A ONLY. Please DON'T use it for advertising, etc.
|Try our online
PLC Simulator- FREE.
Click here now to try it.
New Here? Please read this important info!!!
|December 16th, 2005, 09:11 AM||#1|
Join Date: Dec 2005
Allen Bradley RIO
Thanks for your interest!
Does anyone know how to determine the scan frequency of the flexbus remote I/O mechanism. Does it occur asynchronously to the PLC scan time? At the moment I'm only interested in discrete I/O. Its my understanding that analog I/O must be read using BTs. Perhaps I just dont fully understand the mechanism in which case please explain it!
As an example, I have an SLC5/05 with a 1794-SN installed in Rack 0. A 1794-ASB is intalled and connected with blue hose to the SN. There is a 1794-IB16 on a 1794-TB3 with one wired input to a switch.
Any help is appreciated!
|December 16th, 2005, 10:32 AM||#3|
Lifetime Supporting Member
The adapter scans its I/O on an independent cycle. The main rack's scanner polls the adapters. The processor gets it's copy of the I/O data table from the scanner module during it's I/O scan cycle. In short, the RIO is updated asynchronously to the program scan. The I/O image that the processor is working with does not change during logic solving (with SLCs and PLC5s anyway). With a PLC5, I have read some old A/B manuals that stated that the change of state of a discrete input, for example, may be reported to the processor up to 125ms after it actually occurs. Likewise for an output bit. It may take up to 125ms after the PLC turns on the output before that information reaches the remote output point. Repeatability of this delay is random. It might be 5ms one time and 100ms the next. The number of remote racks will affect this as well. A/B has worksheets that can help you accurately determine maximum RIO delays in their system design manuals.
This is something to always keep in mind at design time. Always try to put your time critical I/O in the local rack.
Hope this helps.
|Currently Active Users Viewing This Thread: 1 (0 members and 1 guests)|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Learning Allen Bradley||mbferrari||LIVE PLC Questions And Answers||9||March 11th, 2009 11:25 AM|
|Allen Bradley 1746-BTM||ChuckM||LIVE PLC Questions And Answers||20||January 28th, 2008 07:16 AM|
|Wincc 6.0 and Allen Bradley PKTX 1784.||nistam||LIVE PLC Questions And Answers||1||March 31st, 2004 10:19 AM|
|Need Help with allen bradley mneumonic explanation||Ctrayler||LIVE PLC Questions And Answers||3||February 26th, 2004 01:23 PM|
|Allen Bradley 5/40L with local I/O extension||nfvtmeinc||LIVE PLC Questions And Answers||2||June 10th, 2003 09:55 PM|