This board is for PLC Related Q&A ONLY. Please DON'T use it for advertising, etc.
|Try our online
PLC Simulator- FREE.
Click here now to try it.
New Here? Please read this important info!!!
|March 18th, 2003, 02:52 PM||#1|
In cpu 226 using EM235 extension module we are taking 0-20 mA out put
In one application when I0.0 is high current output should go out based on AIW0 (input). if at this stage input is 20mA than out put immediatele jumps from 0 to 20 that is 0 % to 100%. I want to send out put through AQW0 SLOWLY. may be 10% every 10 min.
can any body suggest a program using microwin3.2.
thanks Looking for a reply
|Currently Active Users Viewing This Thread: 1 (0 members and 1 guests)|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Acces Siemens S7-315 by VB||GAEvakYD||LIVE PLC Questions And Answers||13||October 14th, 2008 09:29 AM|
|Problems with Siemens MMC cards||RMA||LIVE PLC Questions And Answers||8||November 24th, 2006 02:52 AM|
|Just another AB to SIemens comm (technical details)||ckchew666||LIVE PLC Questions And Answers||2||February 4th, 2005 12:47 AM|
|Siemens S7-313 to OP270B Communication||qee||LIVE PLC Questions And Answers||4||December 18th, 2003 06:40 AM|
|Siemens Cpu226||UTPAL CHATTERJEE||LIVE PLC Questions And Answers||2||March 19th, 2003 12:17 AM|