This board is for PLC Related Q&A ONLY. Please DON'T use it for advertising, etc.
|Try our online
PLC Simulator- FREE.
Click here now to try it.
New Here? Please read this important info!!!
|September 23rd, 2008, 12:30 PM||#1|
Join Date: May 2007
Control Logix Redundancy
I am having problem in synchronization of redundant chassis. As per redundancy bundle V15.57 package i have update firmware as below
Slot 0 Ethernet module 4.3.2
Slot 1 1756-L61 15.57
Slot 2 1756-CNB/E 11.02
Slot 3/4 empty
Slot 5, 6 1757-SRM 4.4
Well i have done the scheduling of control net..its working fine.. when i eject both ENBT card from both redundant chassis ...then both SRM module get synchronized ..as soon as i inject these ENBT modules then SYNCHRONIZATION gets terminated...
When i start synchronization from Rslinx then i get message......module configuration error......ENBT module has disqualified request for synchronization
I have upadate firmware of ethernet module many times...........Also i have changed the firmwares of all modules as per redundancy bundle of V15.60 but m getting same message
|September 23rd, 2008, 02:36 PM||#2|
Lifetime Supporting Member + Moderator
Do you have the 1756-ENBT modules set for the same IP address ? The -SRMs are supposed to manage them (primary=IP, secondary= IP+1) and you're supposed to set them up the same.
That's all I can think of offhand. Redundancy systems are complex enough that you ought to call RA Tech Support and have them help you through the codes reported by the Redundancy Module tool.
|Currently Active Users Viewing This Thread: 1 (0 members and 1 guests)|
|Thread||Thread Starter||Forum||Replies||Last Post|
|SLC Rack Connect to A control Logix plc||Donnchadh||LIVE PLC Questions And Answers||7||November 24th, 2007 07:48 AM|
|Rmc100 - Enet Setup - Control Logix||drawson||LIVE PLC Questions And Answers||5||August 9th, 2005 07:19 AM|
|Control Logix scan time...||darrenj||LIVE PLC Questions And Answers||23||June 1st, 2005 12:13 PM|
|Need Control Logix Help||Maverick 250||LIVE PLC Questions And Answers||19||May 9th, 2005 11:41 PM|
|Memory Allocation in Control Logix||Ashwin||LIVE PLC Questions And Answers||7||March 4th, 2004 11:44 PM|