This board is for PLC Related Q&A ONLY. Please DON'T use it for advertising, etc.
|Try our online
PLC Simulator- FREE.
Click here now to try it.
New Here? Please read this important info!!!
|February 24th, 2005, 02:55 PM||#1|
Siemens CPU313C Analog Inputs
I am new to Siemens S7300 (313C CPU) PLC and I cannot find the documentation related to analog inputs connecting diagrams.
I have a couple of active flow transmitters (4-20 mA) 120Vac powered, which I would like to connect to the PLC AIs, I have connected passive transmitters before to the same inputs (following the diagram on the module cap), but I am afraid that it might not be the same connection type for active 4-20mA transmitters (no 24 Vdc powers the 4-20mA loop).
If anyone does have connecting diagrams available or any web link, please help. I appreciate it.
|February 25th, 2005, 03:02 AM||#3|
Lifetime Supporting Member + Moderator
In the above example (for channel 2) you would have to connect the 4-20mA signal on pin 9.
If you use channel 0, you will have to connect the 4-20mA signal on pin 3.
Connect ground to pins 4-7-10-13-20. The ground must be looped back to the device that generates the 4-20 mA signal.
3 strikes and you're out
|Currently Active Users Viewing This Thread: 1 (0 members and 1 guests)|
|Thread||Thread Starter||Forum||Replies||Last Post|
|S7 300 SM331 Analog Inputs Problem; Relative DC leval of adjacent inputs.||David Torrens||LIVE PLC Questions And Answers||4||November 10th, 2004 10:14 AM|
|siemens analog inputs||GTX||LIVE PLC Questions And Answers||12||March 13th, 2004 10:50 PM|
|Siemens Analog Inputs||KA24DE||LIVE PLC Questions And Answers||5||February 4th, 2004 05:05 AM|
|Siemens Analog Inputs Shared||Kthiel||LIVE PLC Questions And Answers||0||July 3rd, 2002 01:29 AM|