This board is for PLC Related Q&A ONLY. Please DON'T use it for advertising, etc.
|Try our online
PLC Simulator- FREE.
Click here now to try it.
New Here? Please read this important info!!!
|December 21st, 2011, 11:49 AM||#1|
Join Date: Dec 2011
Connecting to a PLC-5/10
I must admit I have limited knowledge of PLCs and their communictaion protocols. I am looking for some help on connecting to two PCL-5/10 units. We seem to have misplaced our DH+ card & cable so our HQ sent us a 1784-PCMK A card, but no cable. We also have a 1784-PCD C card. I am assuming that if we get the correct cable we could use the 1784-PCMK A card to connect to the PLC-5/10? I am also assuming that we can't use the 1784-PCD C card for this? We have all the software, just no way to connect to these directly.
Thanks in advance,
|December 21st, 2011, 12:31 PM||#2|
Lifetime Supporting Member + Moderator
You are correct about the 1784-PCD card; it is only for DeviceNet.
The 1784-PCMK Series A card requires a 1784-PCM5 Series A cable to connect to the PLC-5/10 (this is a "Classic" PLC-5).
PCMK Series A cards require Series A cables; the wide, flat connector is different from the Series B cables.
The 1784-PCM5 has a "DB9" style connector that looks like an RS-232 serial port but is actually Data Highway Plus on a "Peer Communication Link" (PCL) connector, which is what the connector on the PLC-5/10, 5/12, 5/15, 5/25 controllers is for.
|Currently Active Users Viewing This Thread: 1 (0 members and 1 guests)|
|Thread||Thread Starter||Forum||Replies||Last Post|
|Connecting to subunits on a siemens S5 PLC||yogiontour||LIVE PLC Questions And Answers||3||August 15th, 2011 03:17 AM|
|Problem with connecting s7 319 PLC and PC station||b00c||LIVE PLC Questions And Answers||0||May 12th, 2009 11:17 AM|
|connecting a directional valve to PLC||muzikant5||LIVE PLC Questions And Answers||11||April 14th, 2009 09:51 AM|
|Cannot Communicate with PLC Error while connecting to FX2-48MT||pdk153||LIVE PLC Questions And Answers||1||November 30th, 2008 03:43 AM|
|Connecting S7 200 PLC with PC||Unregistered||LIVE PLC Questions And Answers||5||May 12th, 2005 01:40 AM|